For Fine Particle Removal from WaterUltipleat High Flow filter elements are designed for high particle removal efficiency of fine particulates from water applications. The Ultipleat High Flow filter elements utilize polyethersulfone (PES) media with unique, laid-over pleat geometry. The Ultipleat High Flow element is a large diameter, single open ended, pleated cartridge with an inside to outside flow pattern and a core-free construction. The filter's unique laid-over pleat geometry, combined with its large diameter means fewer elements are required for a given flow rate when compared to standard diameter cartridges. Filter vessels are correspondingly smaller, resulting in lower capital and installation costs, as well as reduced operating costs.
|Polyethersulfone membrane with no adhesives or surfactants|| |
|Pleated (laid-over pleat geometry) media in a large diameter cartridge format|| |
|Inside to outside flow configuration||At element change-out, protects filtrate from recontamination by trapping particulates inside the cartridge|
1Typical when compared to standard cartridges used in test comparison.
Food Contact Compliance
- Food contact compliant filters are available. Please consult the Declarations of Compliance for applicable part numbers at the links below.
- Ultipleat Filter Element Declaration of Compliance
Ultipleat Filter Element Construction (Showing Uniform Flow Distribution)
Materials of Construction
- Filter Medium: Pre-filtration layer Pall proprietary melt blown polypropylene media, Final filtration layer Pall proprietary Supor® PES membrane (polyethersulfone)
- Support Mesh and Outer Wrap: Polypropylene
- End Caps and Handle: Polypropylene (10% glass fiber reinforced)
- O-ring Seal: Ethylene propylene rubber
Operating Characteristics in Compatible Fluids2
|Maximum Differential Pressure||Max. Operating Temperature3|
|3.45 bard (50 psid) (forward direction)||82 °C (180 °F)|
|Hot Water||85-90 °C (185-194 °F)||10 hours|
|320 ppm total peroxides||20 °C (68 °F)|
Typical Flow Rates5
2Compatible fluids are defined as those which do not swell, soften or attack any of the filter components.
3Not recommended where the temperature is cycled more than 10 °C (50 °F).
4Measured under laboratory test conditions. Users should verify suitability against their own conditions of use. Where indicated 10 minute sanitization cycles were utilized.
5Typical initial clean media differential pressure (Δp) per 1016 mm (40 in.) and 1524 mm (60 in.) cartridge for water at 20 °C (68 °F); viscosity 1 centipoise. For assistance in filter assembly sizing and housing selection, contact your Pall representative.
- Cartridges produced in a controlled environment
- Manufactured according to ISO 9001:2008 certified Quality Management System
Example Part Number: HFU 6 40CAS010 JUW (See bold references in tables below.)
Part Number: HFU 6 < Length Code from Table 1 > CAS010 JUW
Table 1 - Nominal Length
|40||1016 mm (40”)|
|60||1524 mm (60”)|
Outside to in flow is not recommended. Ultipleat High Flow filter elements are designed for water flow rates typically >10 m3/h (44 US gpm), please contact your Pall representative for product recommendations more suitable to lower flow rates.